Commercial eight inch horizontal down light rated for use with one quad or triple tube lamp. Use in non insulated ceiling, where insulation can be kept 3" from fixture, and 1/2" from adjacent building components. Adheres to the minimum lumens to watts ratio that qualifies to Energy Star.
Plaster Frame: Architectural quality 0.050 galvanized steel ring riveted to elevated 0.064 steel junction box and ballast tray.
Clearance: Non-IC frame-ins require a minimum clearance of 3" around from thermal insulation and 1/2" from combustible material from above the fixture.
Socket Cup: Die-cast formed galvanized steel with one 4-pin socket. The socket cup attaches to the finishing trim with two present screws that allow for minor rotation within two keyhole slots and a third fixed position anchor screw.
Bar Hangers: Two 13-3/4" to 24-1/2" adjustable bar hangers with captive nails are included on frame. Bar hangers are parallel to junction box